Search Results: “” — Page 1
Wark, Bob; Thomas, Louise
This paper discusses the rating curves developed for several case studies from the Pilbara and Kimberley, including the Harding Dam, Moochalabra Dam and Ophthalmia Dam. The paper will discuss the impact of underestimated rating curves on the design of infrastructure. An example has occurred at Harding Dam where the pump station was designed to be inundated at a 1:100 AEP and this is now estimated to occur at a lower AEP. The paper will also discuss methods to improve the accuracy of rating curves and the challenges associated with determining accurate rating curves.
Now showing all 2 search results
2015 – Sweet Smell of Successful Risk ManagementLearn more
Jason Fowler, Robert Wark
Tropical Forestry Services (TFS) currently (2015) leases Arthur Creek Dam from the West Australian state government and utilises the water source to drip irrigate its Indian sandalwood (Santalum album) plantation. Arthur Creek Dam is located approximately 70 km south west of Kununurra in the East Kimberley region of Western Australia. TFS grows and processes the sandalwood to produce oil that is used extensively in the global fragrance perfume market. TFS took over the lease of the 26 m high zoned earth core and rock fill dam in 2007 and has systematically carried out remedial works to the structure to lower the f-N curve below the ANCOLD “Limit of Tolerability” and to well within the ALARP zone. This paper describes the proactive risk management approach TFS has undertaken to address dam safety issues. It also specifically describes the most recent management issue, being the outlet pipe refurbishment.Learn more
A number of dam safety issues were identified during the initial surveillance and subsequent annual surveillance inspections. Issues include insufficient spillway capacity, seepage from the right abutment and deterioration of the steel outlet pipe. The remedial works to the outlet pipe were completed in late 2014 and involved close collaboration between TFS, the contractor and the designer. The outlet pipe re-sleeving operation was complex as the dam had to remain in operation and the water level could not be artificially lowered. In addition, the original outlet pipe was asymmetrical along both the vertical and horizontal axes, close to the bulkhead gate structure. Contingency measures were employed to enable the dam to remain in operation with 3 DN 400 HDPE siphon pipes installed.
The completion of the refurbishment of the outlet pipe by sleeving the pipe reduced the risk posed by this structure by an order of magnitude. Planned future risk reduction measures include the treatment of seepage within the upper right abutment and rebuilding the crest. These actions will further reduce the risk of dam failure through piping and overtopping of the dam crest.
Keywords: risk, ALARP, outlet pipe, re-sleeving.