Frank L Burns
By 1976 head loss in the 23 km long 750/900 mm diameter CLMS pipeline from Eppalock Reservoir to Bendigo had increased from 45.7 m to 98.2 m (115%) after only 12 years service. The cause was identified as increased friction from soft voluminous iron and manganese bacterial slime building up on the pipe walls and increasing the friction. Inspection of the drained pipes in the dry gave little indication of the problem since the slime consolidated to an innocuous looking thin smooth coating as it dried.
1960 studies by Tyler and Mitchell at the University of Tasmania for the Hydro-Electric Commission had shown that the micro-organisms producing these slime growths were present in all pipelines. However they required the presence of iron and manganese in the water to flourish and produce flow reduction. Remobilisation from oxygen deficient bottom sediments was shown in the 1940’s by Pearsall and Mortimer in England to be a major source of iron and manganese in reservoir water and this could be controlled if sufficient dissolved oxygen could be provided to convert the reducing conditions at the sediments to oxidising conditions.
An experimental aeration system designed by the author was operated in the 180,000 ML Eppalock Reservoir for 19 days during March 1977. This mixed the reservoir to the depth of the aerators (24 m) increasing the low 10% saturation dissolved oxygen at this depth to a high 94% saturation thereby changing chemical conditions from reducing to oxidising. As a result the iron concentration in the surface water decreased from 2.04 mg/L to 0.54 mg/L but there was little change in the pre-aeration 0.03 mg/L manganese concentration with this short period of aeration. The iron concentration in the water flowing in the pipeline changed from 1.78 mg/l to 0.57 mg/l.
The problem of pipe flow reduction from bacterial slime growth on the pipe walls is discussed in this paper and examples are given of the use of automatic reservoir aeration to overcome the problem including costs and results.
The RCC design review and construction supervision of the 60m high Tannur Dam in Jordan was carried out by GHD, Australia.
The 220,000m3 of RCC was placed during February-December 2000; change to the sloped layer method was made once the dam reached 15m height. It produced a 50% increase in placing rate and a considerable saving in costs.
The use of the method is the first known use outside of China, where it was developed during the construction of the 130m high Jiangya Dam in 1997-8. The sloping of the 300mm thick layers of RCC across the dam from bank to bank at grades between 5-8% ensures subsequent layers of RCC can be placed within the initial set time of the lower layer and hence the RCC is monolithic across the lift joint.
This paper briefly describes the project in Jordan and then gives specific details of the use of the sloped layer method. Typical results from the quality control testing during placement and subsequent coring and testing of the lift joints are also provided. The benefits of its use in adverse climatic conditions, such as extreme heat or rainfall and the ways it can be integrated with forming the upstream-downstream slope are also discussed.
The sloped layer method is a significant advancement, particularly for large structures, where lift joint cohesion, tensile resistance and RCC placing rates are vitally important.
M G Webby
Investigations of damaging blowback incidents at the headrace tunnel intake to Rangipo Power Station in the Central North Island of New Zealand are described. The blowback phenomenon is explained theoretically based on evaluation of the evidence available from the incidents and information obtained from the literature. A physical hydraulic model study is described in which this explanation of the blowback phenomenon was verified. The model was also used to devise a solution for the blowback problem.
Assessment of dam safety requires estimates of extreme rainfall together with the temporal and spatial distributions of extreme rainfall. In order to satisfy dam safety requirements for dams in the west coast of Tasmania, the Bureau of Meteorology has developed the method of storm transposition and maximisation for application in this region.
Daily, as well as continuously recorded rainfall data for all Bureau of Meteorology and Hydro Tasmania sites in western Tasmania have been analysed and the most outstanding rainfall events over one, two and three-day durations in the region have been identified. Meteorological analysis of these events reveals that the most significant rainfall events in the west coast of Tasmania are caused by the passage of fronts, which are sometimes associated with an intense extratropical cyclone, with a westerly or southwesterly airstream.
A database of isohyetal analyses of the most significant rainfall events in western Tasmania has been established. These can be used either ‘in situ’ or transposed to estimate mean catchment rainfall. Storm dewpoint temperatures for the purpose of moisture maximisation have been determined.
Cumulative and incremental three-hourly temporal distributions for sites having continuous rainfall data or three-hourly meteorological observations have been constructed and design temporal distributions of extreme rainfall have been derived.
An objective method for adjusting for differences in the topography between the storm and target locations is proposed
Dam safety emergency plans (DSEPs) are typically produced for individual dams. For owners of a large portfolio of dams, this approach creates document control difficulties, requires excessive time and effort and can lead to confusion when a single emergency affects multiple dams having individual DSEPs. Hydro Tasmania has developed a single DSEP which is applicable to its portfolio of 54 referable dams. The DSEP contains generic emergency response procedures, is applicable to a whole range of generic dam safety incidents, uses a simple colour-coded flowchart-action list format, has a two-stage emergency response, retains all necessary dam-specific information and can be easily adapted to any organisational structure. This approach was found to have benefits in document control, flexibility in the management of the emergency response and short lead time in terms of having DSEPs which cover an entire portfolio of dams.