The disused Stapylton quarry is located in the suburbs of the Queensland Gold Coast. Gold Coast City Council, as part of the Northern Wastewater Strategy, has included the use of the quarry for storage and re-distribution of reclaimed water from the Beenleigh Water Reclamation Facility (WRF) to the downstream cane farmlands. A comprehensive EIS has been produced, which has strict water quality requirements for the quarry environs as well as the reservoir and outflow. This paper presents the background to the Northern Wastewater Strategy, the requirements for the Stapylton reservoir and the analysis performed for the detailed design of the embankment dam and the inlet bubble plume destratification system. The modelling of the destratification system was undertaken using the programme DYnamic REservoir Simulation Model (DYRESM) coupled with Computational Aquatic Ecosystems DYnamics Model (CAEDYM). The outcomes and implications of the modelling for the design and system operation including environmental monitoring are discussed.
John Grimston, Robin Dawson, Maurice Fraser
Water supply for irrigation of horticulture and agriculture in New Zealand has gained considerable momentum since the mid 1990’s. The rapid growth of the wine industry in areas such as Marlborough (located at the top of the South Island) and dairy conversions in many areas of South Canterbury are prime examples of the pressure being applied to existing water supplies and sources and the increasing need for new irrigation supplies and security of supply.
The larger irrigation projects of the past were implemented by the government – schemes such as the Rangitata Diversion race and the Lower Waitaki irrigation project both on the east coast of the South Island. The 1990’s and early 2000’s has seen a largely hands off government approach to potential irrigation projects with the shift towards leaving it to market forces to build irrigation schemes. The result has been that due to significant larger project risks and capital cost requirements with often multi party stakeholder groups, only relatively small schemes have been implemented – the Waimakariri irrigation scheme and Opuha irrigation dam are a few examples. However, in recent years with the value of water increasing several significant irrigation projects promoted by private enterprise or progressive district councils with farmer groups are being investigated and a few may be close to implementation.
The recent drought conditions have focussed attention on the need for storages to maintain security of supply and, together with the balance with sustainability, the consenting environment in New Zealand and existing river/aquifer allocations, significant challenges to development are presented.
Specific case examples include the proposed Delta dam near Blenheim being developed by a private group of irrigators and the Bankhouse development being implemented by a private owner in the same Marlborough region.
This paper provides a background to irrigation in the South Island and describes these two proposed schemes and associated storage dams, together with an insight into the key issues related to the proposed projects.
Frank L Burns
By 1976 head loss in the 23 km long 750/900 mm diameter CLMS pipeline from Eppalock Reservoir to Bendigo had increased from 45.7 m to 98.2 m (115%) after only 12 years service. The cause was identified as increased friction from soft voluminous iron and manganese bacterial slime building up on the pipe walls and increasing the friction. Inspection of the drained pipes in the dry gave little indication of the problem since the slime consolidated to an innocuous looking thin smooth coating as it dried.
1960 studies by Tyler and Mitchell at the University of Tasmania for the Hydro-Electric Commission had shown that the micro-organisms producing these slime growths were present in all pipelines. However they required the presence of iron and manganese in the water to flourish and produce flow reduction. Remobilisation from oxygen deficient bottom sediments was shown in the 1940’s by Pearsall and Mortimer in England to be a major source of iron and manganese in reservoir water and this could be controlled if sufficient dissolved oxygen could be provided to convert the reducing conditions at the sediments to oxidising conditions.
An experimental aeration system designed by the author was operated in the 180,000 ML Eppalock Reservoir for 19 days during March 1977. This mixed the reservoir to the depth of the aerators (24 m) increasing the low 10% saturation dissolved oxygen at this depth to a high 94% saturation thereby changing chemical conditions from reducing to oxidising. As a result the iron concentration in the surface water decreased from 2.04 mg/L to 0.54 mg/L but there was little change in the pre-aeration 0.03 mg/L manganese concentration with this short period of aeration. The iron concentration in the water flowing in the pipeline changed from 1.78 mg/l to 0.57 mg/l.
The problem of pipe flow reduction from bacterial slime growth on the pipe walls is discussed in this paper and examples are given of the use of automatic reservoir aeration to overcome the problem including costs and results.
Craig Johnson, Phillip Solomon, Nihal Vitharana
Tank Hill Reservoir is located approximately 25km north-east of Warrnambool and forms part of the fresh water supply for the town. It was built in the 1930’s by the construction of an earthfill dam across the natural breach of the crater of an extinct volcano. The reservoir is an offline storage with a small natural catchment and has a nominal capacity of 770ML at Full Supply Level (FSL). The reservoir is operated by South West Water Authority (SWWA).
Previous investigations had identified instability issues associated with the dam embankment and the necessity for remedial work to increase the stability of the dam embankment. SKM undertook detailed survey and investigations and the proposed upgrade works include the construction of a downstream stabilising berm incorporating graded filters and a drainage system. The condition of the outlet works was investigated as part of the project, with some of these works found to be in poor condition with a risk to the security of supply, necessitating the design of refurbishment of the outlet works. The degree of siltation of the reservoir was also assessed, and some loss of capacity due to siltation was noted.
Detailed investigations were performed to determine the optimum configuration of the stabilising berm and to locate and test suitable construction materials. The embankment interface filters were designed to satisfy modern filter design criteria and were incorporated in the embankment drainage system. The condition of the outlet works, including the intake standpipe, three offtake valves and the outlet conduit beneath the embankment, were assessed via manual and CCTV inspections. An operation review, incorporating the proposed upgrade works within the framework of ongoing operation of the reservoir for supply to downstream customers was also prepared, as was a construction risk assessment.
This paper will present “extremely useful practical information” for dam design engineers, owners and operators where the whole spectrum of dam safety issues is required for the successful completion of remedial works design and construction.
The RCC design review and construction supervision of the 60m high Tannur Dam in Jordan was carried out by GHD, Australia.
The 220,000m3 of RCC was placed during February-December 2000; change to the sloped layer method was made once the dam reached 15m height. It produced a 50% increase in placing rate and a considerable saving in costs.
The use of the method is the first known use outside of China, where it was developed during the construction of the 130m high Jiangya Dam in 1997-8. The sloping of the 300mm thick layers of RCC across the dam from bank to bank at grades between 5-8% ensures subsequent layers of RCC can be placed within the initial set time of the lower layer and hence the RCC is monolithic across the lift joint.
This paper briefly describes the project in Jordan and then gives specific details of the use of the sloped layer method. Typical results from the quality control testing during placement and subsequent coring and testing of the lift joints are also provided. The benefits of its use in adverse climatic conditions, such as extreme heat or rainfall and the ways it can be integrated with forming the upstream-downstream slope are also discussed.
The sloped layer method is a significant advancement, particularly for large structures, where lift joint cohesion, tensile resistance and RCC placing rates are vitally important.
Peter D Amos, Thomas G Newson, Murray D Gillon
In September 2000, pressures being monitored in a geological fracture beneath Arapuni Dam were found to be rising significantly, indicating that a deteriorating condition was developing in the foundation. Two boreholes drilled in 1995 had intersected high water pressures within the fracture in an area close to the downstream face of the dam, posing a risk of major leakage developing from where the fracture day-lighted downstream of the dam. Lumps of clay, bitumen and lake biota, including snails and small fish, were identified discharging from the boreholes, indicating that a significant leakage path had developed. Detailed investigations, the subject of this paper, were carried out from September 2000 to confirm the extent and nature of the deterioration. A range of groundwater investigation techniques and tools were used, while the reservoir remained full, to identify the source of the leak and confirm the path it took. The investigations culminated in development of a groundwater model that described the seepage behaviour in the dam foundation. Based on the investigation information gathered, the foundation fracture bearing the high water pressure was successfully grouted in December 2001 without lowering the reservoir.