M. Barker, T. Burt, K. McCallum-Gaul, Dr M. Barry
The disused Stapylton quarry is located in the suburbs of the Queensland Gold Coast. Gold Coast City Council, as part of the Northern Wastewater Strategy, has included the use of the quarry for storage and re-distribution of reclaimed water from the Beenleigh Water Reclamation Facility (WRF) to the downstream cane farmlands. A comprehensive EIS has been produced, which has strict water quality requirements for the quarry environs as well as the reservoir and outflow. This paper presents the background to the Northern Wastewater Strategy, the requirements for the Stapylton reservoir and the analysis performed for the detailed design of the embankment dam and the inlet bubble plume destratification system. The modelling of the destratification system was undertaken using the programme DYnamic REservoir Simulation Model (DYRESM) coupled with Computational Aquatic Ecosystems DYnamics Model (CAEDYM). The outcomes and implications of the modelling for the design and system operation including environmental monitoring are discussed.
This paper presents the findings of experimental investigation of internal erosion by the process of suffusion within embankment dams and their foundations.
Suffusion is the process by which finer soil particles are moved through constrictions between larger soil particles by seepage forces. Soils susceptible to suffusion are usually described as internally unstable. Understanding of the suffusion process is important to the assessment of the risk of internal erosion in an embankment dam and its foundation. Suffusion results in a coarser soil structure, leading to increased seepage, progressive deterioration of the dam or its foundation, and a higher risk of toe instability. Suffusion within the protective filter of a dam may result in a coarser filter, rendering it ineffective in protecting the core materials from erosion.
Two types of suffusion tests, namely the downflow test and the upflow test, have been conducted at the University of New South Wales. The downflow test aims at identifying the types of soils that are susceptible to suffusion, whereas the upflow test aims at identifying the hydraulic gradient at which suffusion is initiated. This paper presents the initial findings of the downflow test. Eighteen downflow tests have been carried out on fourteen clay-silt-sand-gravel soils. The Kenney and Lau (1985, 86) method, which is commonly used for assessing the internal stability of coarse-grained soils, appears to be too conservative when used to predict the internal stability of silt-sand-gravel or clay-silt-sand- gravel soils, whereas the Burenkova (1993) method appears to provide better predictions. Further testing is required to define more accurate criteria for determining the internal stability of broadly-graded clay-silt-sand-gravel soils.
This paper discusses reliability issues of the fourteen 3.85m high by 7.89m wide radial gates at Glenmaggie Dam in Victoria and the twin 3.6m high by 16.5m wide drum gates at Little Nerang Dam in Queensland. The Glenmaggie dam radial gates are manually controlled using electrically driven (mains and diesel generator power supply) hoist motors with a petrol driven hydraulic pack for use in the event of complete electrical power supply failure. A detailed fault tree analysis was developed for the spillway gate reliability of the Glenmaggie Dam gates as part of the risk assessment for the dam, which was being completed at the time of publishing the paper. Each of the identified components of the spillway gates, including human error in operation was used to evaluate the probability of failure of a single gate or multiple gates for inclusion in the event tree to estimate the risk and assist the evaluation of the requirement for remedial works. The Little Nerang drum gates are fully automatic hydraulically operated gates with independent operating mechanics and a common override system in the event of automatic system failure. Drum gates are uncommon on dams and the system operation is discussed together with an assessment of the reliability and measures taken for handling operating risks during floods for the dam, which has some stability concerns.
State Water # as manager of Keepit Dam has established a comprehensive upgrade project.
A portfolio risk assessment by State Water of its major dams placed Keepit Dam as the highest priority for an upgrade.
While extreme flood and earthquake dam safety are the main drivesr for this upgrade, the opportunity has been taken to integrate other key dam management considerations into the process including environmental improvements, flood mitigation and sustainable regional development.
The dam, which is located on the Namoi River some 45km upstream of Gunnedah, is, in tandem with Split Rock Dam upstream, a vital irrigation water supply for the Namoi Valley region in northern New South Wales.
In considering the most appropriate way of addressing the critical flood safety issue, it became very apparent that the solutions were many and they significantly impacted on the local community. Other important issues such as water quality and flood mitigation, and overall sustainable development in the valley, particularly system water reliability, could influence dam safety solutions and so also needed to be considered as part of the process. As such it was considered imperative that the local community be actively involved in determining both interim and long-term upgrade solutions.
To achieve the best outcome for the region, State Water since mid 2001, has used the community consultation approach to guide the project.
Currently interim works have been completed and long-term options are being evaluated.
An Environmental Impact Statement on the preferred proposal will be undertaken during the later part of 2004 and if approved, all works will be completed by end of 2007.
This paper will highlight our experiences to date including:
• the proposition of an integrated consultative process;
• the background to the project;
• the need for and extent of upgrade;
• an integrated consultation and communication approach including innovative processes and the creation of a high profile Community Reference Panel (CRP) to guide the upgrade project;
• some dos and don’ts from a consultation perspective, for use in other upgrade projects; and
• where to from now.
This paper provides an insight into the management of reservoirs under drought conditions within the new water management frameworks established under the Council of Australian Governments (COAG) Water Reforms. Traditional approaches to the sharing of available supplies during drought are no longer appropriate as the roles of the resource regulator, infrastructure operator, and Government have been separated in the interests of providing certainty for water users and the environment. Recent experiences during drought in the Upper Mary River system near Gympie in Queensland has demonstrated the need to ensure the robustness of water sharing rules for reservoirs under the new framework if certainty is to be delivered.
The Bureau of Meteorology has recently revised the Probable Maximum Precipitation (PMP) estimates for the Generalised Tropical Storm Method (GTSM) region of Australia. The revision process has involved the application of the more technically rigorous Generalised Southeast Australia Method (GSAM) that was previously developed for the southern part of Australia to a much larger data set of severe tropical storms. This has generally lead to an increase in the total GTSM PMP depths with a resultant increase in the Probable Maximum Precipitation Design Flood (PMPDF) and the Probable Maximum Flood (PMF).
In addition, the revision process has produced significant modifications to the temporal and spatial patterns adopted when applying the PMP depths to a dam’s catchment and these changes have also generally lead to increases in the resultant floods.
This paper discusses the rationale behind the increases in PMP depths and changes in the associated temporal and spatial patterns and presents the justification for the adoption of these more scientifically defensible estimates.
The application of the revised PMP estimates to the Keepit Dam catchment in northern NSW is presented and a comparison between the PMPDF and PMF estimates based on the original GTSM and the revised GTSM (GTSMR) made for this specific case study.