There are many important dams and other structures on catchments smaller than 1000 km² with response times less than 24 hours, however these catchments have been largely overlooked in previous research into large and extreme floods. This paper is an initial step in “catching up” design practice for short duration rainfall events to the current best practice that is available for estimation of floods from rainfall events with durations of 24 hours and greater.
Two issues are specifically addressed in this paper. Firstly, a regional analysis of short duration rainfall depths is conducted to extend the frequency curve beyond an AEP of 1 in 100. Rainfall frequency curves are estimated for durations between 0.5 and 12 hours, using data from ten pluviograph sites around Australia. Secondly, sets of temporal patterns are derived that could be useful in joint probability analysis of short duration rainfall events. The effects of these new rainfall depths and temporal patterns on flood frequency curves are tested by applying them to rainfall-runoff routing models for three dams with small catchment areas.
Now showing 1-12 of 72 2967:
Frank L Burns
By 1976 head loss in the 23 km long 750/900 mm diameter CLMS pipeline from Eppalock Reservoir to Bendigo had increased from 45.7 m to 98.2 m (115%) after only 12 years service. The cause was identified as increased friction from soft voluminous iron and manganese bacterial slime building up on the pipe walls and increasing the friction. Inspection of the drained pipes in the dry gave little indication of the problem since the slime consolidated to an innocuous looking thin smooth coating as it dried.
1960 studies by Tyler and Mitchell at the University of Tasmania for the Hydro-Electric Commission had shown that the micro-organisms producing these slime growths were present in all pipelines. However they required the presence of iron and manganese in the water to flourish and produce flow reduction. Remobilisation from oxygen deficient bottom sediments was shown in the 1940’s by Pearsall and Mortimer in England to be a major source of iron and manganese in reservoir water and this could be controlled if sufficient dissolved oxygen could be provided to convert the reducing conditions at the sediments to oxidising conditions.
An experimental aeration system designed by the author was operated in the 180,000 ML Eppalock Reservoir for 19 days during March 1977. This mixed the reservoir to the depth of the aerators (24 m) increasing the low 10% saturation dissolved oxygen at this depth to a high 94% saturation thereby changing chemical conditions from reducing to oxidising. As a result the iron concentration in the surface water decreased from 2.04 mg/L to 0.54 mg/L but there was little change in the pre-aeration 0.03 mg/L manganese concentration with this short period of aeration. The iron concentration in the water flowing in the pipeline changed from 1.78 mg/l to 0.57 mg/l.
The problem of pipe flow reduction from bacterial slime growth on the pipe walls is discussed in this paper and examples are given of the use of automatic reservoir aeration to overcome the problem including costs and results.
The paper highlights the fundamental importance of correct data selection and storage for the quality of Asset Management demanded for today’s water industry infrastructure.
In developing this theme, the concept of Risk driven maintenance is introduced to focus attention on those issues that not only the identify the appropriate data to be collected and stored, but also, by way of illustrated examples, the direct relevance and application of reliability engineering principles in Risk Analysis.
The author’s principle objective is to demonstrate that the historical data on reliability, condition and performance must be supported with detailed costing information if any worthwhile outcomes are to be forthcoming from analysis.
This paper provides an insight into the management of reservoirs under drought conditions within the new water management frameworks established under the Council of Australian Governments (COAG) Water Reforms. Traditional approaches to the sharing of available supplies during drought are no longer appropriate as the roles of the resource regulator, infrastructure operator, and Government have been separated in the interests of providing certainty for water users and the environment. Recent experiences during drought in the Upper Mary River system near Gympie in Queensland has demonstrated the need to ensure the robustness of water sharing rules for reservoirs under the new framework if certainty is to be delivered.
Sydney Catchment Authority (SCA) has been progressively enhancing its asset management capability for dams and other headworks infrastructure since 1999. A key to the development of the integrated asset management system has been the application of asset condition assessment and Failure Modes, Effects and Criticality Analysis (FMECA) across the water supply mechanical and electrical assets. This has provided vital data necessary to:
• Identify all the mechanical and electrical assets
• Update the computerised maintenance management system database (MAXIMO)
• Determine asset criticality against a range of factors
• Allow review and rationalisation of maintenance work plans
• Upgrade the System Management Plans
Asset management features as a key result area within the SCA’s Corporate Business Plan. Integrated asset management is achieved by cascading corporate outcomes, strategies, objectives and responsibilities down through divisional and team work plans to individual staff members. This paper covers a range of issues that have a bearing on the day-to-day integrity of the infrastructure required to deliver bulk raw water to the SCA’s customers.
The management of maintenance at Warragamba Dam is used as an example to demonstrate the effectiveness and practicality of the application of the contemporary asset management system.
South East Queensland Water Corporation (SEQWater) as owner and operator is proceeding with an upgrade of the flood capacity of Wivenhoe Dam. SEQWater has formed an Alliance with Leighton Contractors, Coffey Geosciences, Montgomery Watson Harza (MWH) and the Department of Commerce-NSW (formerly DPWS, NSW) to upgrade Wivenhoe Dam. This paper presents feasibility level investigation and design activities for an upgrade option, comprising a large labyrinth auxiliary spillway at the right abutment of the dam, for supplementing the existing gated spillway in handling the Probable Maximum Flood (PMF) event. This right abutment auxiliary spillway option incorporates Hydroplus type concrete fuse gates. The investigation so far has proved the technical viability of this option, however, ranking along with the other three options against various criteria will lead to the selection of the preferred upgrade option.