This paper provides an insight into the management of reservoirs under drought conditions within the new water management frameworks established under the Council of Australian Governments (COAG) Water Reforms. Traditional approaches to the sharing of available supplies during drought are no longer appropriate as the roles of the resource regulator, infrastructure operator, and Government have been separated in the interests of providing certainty for water users and the environment. Recent experiences during drought in the Upper Mary River system near Gympie in Queensland has demonstrated the need to ensure the robustness of water sharing rules for reservoirs under the new framework if certainty is to be delivered.
Now showing 1-12 of 72 2967:
Frank L Burns
By 1976 head loss in the 23 km long 750/900 mm diameter CLMS pipeline from Eppalock Reservoir to Bendigo had increased from 45.7 m to 98.2 m (115%) after only 12 years service. The cause was identified as increased friction from soft voluminous iron and manganese bacterial slime building up on the pipe walls and increasing the friction. Inspection of the drained pipes in the dry gave little indication of the problem since the slime consolidated to an innocuous looking thin smooth coating as it dried.
1960 studies by Tyler and Mitchell at the University of Tasmania for the Hydro-Electric Commission had shown that the micro-organisms producing these slime growths were present in all pipelines. However they required the presence of iron and manganese in the water to flourish and produce flow reduction. Remobilisation from oxygen deficient bottom sediments was shown in the 1940’s by Pearsall and Mortimer in England to be a major source of iron and manganese in reservoir water and this could be controlled if sufficient dissolved oxygen could be provided to convert the reducing conditions at the sediments to oxidising conditions.
An experimental aeration system designed by the author was operated in the 180,000 ML Eppalock Reservoir for 19 days during March 1977. This mixed the reservoir to the depth of the aerators (24 m) increasing the low 10% saturation dissolved oxygen at this depth to a high 94% saturation thereby changing chemical conditions from reducing to oxidising. As a result the iron concentration in the surface water decreased from 2.04 mg/L to 0.54 mg/L but there was little change in the pre-aeration 0.03 mg/L manganese concentration with this short period of aeration. The iron concentration in the water flowing in the pipeline changed from 1.78 mg/l to 0.57 mg/l.
The problem of pipe flow reduction from bacterial slime growth on the pipe walls is discussed in this paper and examples are given of the use of automatic reservoir aeration to overcome the problem including costs and results.
Hydro Tasmania has recently upgraded the control systems for the spillway gates of three of its dams, Clark Dam, Meadowbank Dam and Liapootah Dam. The upgrades followed internal reliability assessments that highlighted high reliance on operator attendance, single points of failure and operational difficulties on each of the three gate systems.
The three gates are of contrasting types. Clark Dam Spillway Gates are submerged orifice type radial gates, operated by wire rope hoists. Meadowbank Crest Gates are flap type gates, held by 10 hydraulic cylinders per gate, a design that has had a difficult operating history. Liapootah is a floating drum gate. The upgrades for each gate therefore required different solutions, albeit within a common basis of design framework. The solutions arrived at are innovative, and meet or exceed worlds best practice.
All three gates are now fully automatic, with PLC control. The use of PLC’s significantly enhances the reliability of the gates. Extensive use is also made of the PLC in monitoring key systems. For example, an impossibly rapid lake level rise detected by one transducer, but not its duplicate, will be alarmed but ignored to avoid unnecessary discharge. All systems incorporate appropriate redundancy. The PLC systems also provide some automatic functional testing functionality and enhance remote alarms and local fault finding.
Mechanical systems were modified to facilitate automation and increase reliability. Stand by power sources used include auto-start diesel genset, DC batteries and a micro hydro generator.
The design and implementation of each of the upgrades was carried out by the Electrical and Mechanical Group of Hydro Tasmania’s Consulting Division, in conjunction with Generation Division’s Project Management Group.
The Bureau of Meteorology has recently revised the Probable Maximum Precipitation (PMP) estimates for the Generalised Tropical Storm Method (GTSM) region of Australia. The revision process has involved the application of the more technically rigorous Generalised Southeast Australia Method (GSAM) that was previously developed for the southern part of Australia to a much larger data set of severe tropical storms. This has generally lead to an increase in the total GTSM PMP depths with a resultant increase in the Probable Maximum Precipitation Design Flood (PMPDF) and the Probable Maximum Flood (PMF).
In addition, the revision process has produced significant modifications to the temporal and spatial patterns adopted when applying the PMP depths to a dam’s catchment and these changes have also generally lead to increases in the resultant floods.
This paper discusses the rationale behind the increases in PMP depths and changes in the associated temporal and spatial patterns and presents the justification for the adoption of these more scientifically defensible estimates.
The application of the revised PMP estimates to the Keepit Dam catchment in northern NSW is presented and a comparison between the PMPDF and PMF estimates based on the original GTSM and the revised GTSM (GTSMR) made for this specific case study.
Tony Qiu and Brian A. Forbes
The RCC design review and construction supervision of the 60m high Tannur Dam in Jordan was carried out by GHD, Australia.
The 220,000m3 of RCC was placed during February-December 2000; change to the sloped layer method was made once the dam reached 15m height. It produced a 50% increase in placing rate and a considerable saving in costs.
The use of the method is the first known use outside of China, where it was developed during the construction of the 130m high Jiangya Dam in 1997-8. The sloping of the 300mm thick layers of RCC across the dam from bank to bank at grades between 5-8% ensures subsequent layers of RCC can be placed within the initial set time of the lower layer and hence the RCC is monolithic across the lift joint.
This paper briefly describes the project in Jordan and then gives specific details of the use of the sloped layer method. Typical results from the quality control testing during placement and subsequent coring and testing of the lift joints are also provided. The benefits of its use in adverse climatic conditions, such as extreme heat or rainfall and the ways it can be integrated with forming the upstream-downstream slope are also discussed.
The sloped layer method is a significant advancement, particularly for large structures, where lift joint cohesion, tensile resistance and RCC placing rates are vitally important.
South East Queensland Water Corporation (SEQWater) as owner and operator is proceeding with an upgrade of the flood capacity of Wivenhoe Dam. SEQWater has formed an Alliance with Leighton Contractors, Coffey Geosciences, Montgomery Watson Harza (MWH) and the Department of Commerce-NSW (formerly DPWS, NSW) to upgrade Wivenhoe Dam. This paper presents feasibility level investigation and design activities for an upgrade option, comprising a large labyrinth auxiliary spillway at the right abutment of the dam, for supplementing the existing gated spillway in handling the Probable Maximum Flood (PMF) event. This right abutment auxiliary spillway option incorporates Hydroplus type concrete fuse gates. The investigation so far has proved the technical viability of this option, however, ranking along with the other three options against various criteria will lead to the selection of the preferred upgrade option.