K. Chandler, D. Gill, B. Maher, S. Macnish and G. Roads
SEQWater is the major supplier of untreated water in bulk to Local Governments and industry in the South East Queensland region of Australia, through ownership of Wivenhoe, Somerset and North Pine Dams. Wivenhoe Dam (Lake Wivenhoe) is located on the Brisbane River in Esk Shire. The storage provides both flood mitigation and water supply storage to Brisbane and Ipswich. The water supply storage capacity at full supply level is 1,160 GL. An additional 1,450 GL of storage above full supply level is used for flood mitigation.
Changes to the estimation of extreme rainfall events has resulted in significant increases in the estimates of the PMF since the original design of Wivenhoe Dam. To upgrade the flood security of Wivenhoe Dam, SEQWater has formed an alliance with Leighton Contractors, Coffey Geosciences, MWH and the NSW Department of Commerce.
This paper details the alliance delivery method, the latest estimates of the PMF based on the GTSMR method and details of the two preferred options being finalised by the Alliance.
N. Vitharana, P. Mendis, G. Kusuma and T. Ngo
In 1998, ANCOLD Guidelines entitled “Guidelines for Design of Dams for Earthquake” was issued. The Guideline mainly deals with the seismic aspects of dams and only a basic reference is made to the seismic assessment of intake towers in Section 8.3. Although the much needed and pioneering step taken to introduce this Guideline is to be appreciated and it has covered the seismic aspects of dams, some confusion does exist amongst dam / structural engineers in assessing the seismic performance of concrete intake towers. This is mainly due to the fact the behaviour of reinforced concrete intakes towers is quite different from that of earth or concrete gravity dams. This confusion could potentially lead to gross overestimate of the inertia loads on concrete intake towers resulting in unnecessary expenditure in investigation and remedial works.
The energy dissipation due to inelastic hysteresis behaviour of concrete members results in a great reduction in the inertia loads compared with those calculated with traditional “elastic” analysis methods. This consequently results in significant reductions in bending moments and shear forces on the tower and its foundation. It is very important to understand the basic behaviour of reinforced concrete, considering the composite action of concrete, longitudinal & hoop reinforcing steel, before embarking in sophisticated dynamic analysis the outputs of which are highly dependent on the input parameters.
The authors have developed a methodology in which the hysteresis energy dissipation due to the inelastic behaviour of concrete intake towers is considered. Various criteria were defined for serviceability and ultimate failure modes such as excessive deflection, spalling of concrete, buckling of reinforcing steel. The confinement effect of hoop steel on the core concrete is also considered.
This paper will present the fundamental aspects of seismic behaviour of reinforced concrete structures with practical cases as applied to intake towers. The results showed that the current methods adopted by various Dam Authorities in Australia are cursory and the energy dissipation aspect should be considered, in conjunction with expert advice, before undertaking any remedial works.
By 1976 head loss in the 23 km long 750/900 mm diameter CLMS pipeline from Eppalock Reservoir to Bendigo had increased from 45.7 m to 98.2 m (115%) after only 12 years service. The cause was identified as increased friction from soft voluminous iron and manganese bacterial slime building up on the pipe walls and increasing the friction. Inspection of the drained pipes in the dry gave little indication of the problem since the slime consolidated to an innocuous looking thin smooth coating as it dried.
1960 studies by Tyler and Mitchell at the University of Tasmania for the Hydro-Electric Commission had shown that the micro-organisms producing these slime growths were present in all pipelines. However they required the presence of iron and manganese in the water to flourish and produce flow reduction. Remobilisation from oxygen deficient bottom sediments was shown in the 1940’s by Pearsall and Mortimer in England to be a major source of iron and manganese in reservoir water and this could be controlled if sufficient dissolved oxygen could be provided to convert the reducing conditions at the sediments to oxidising conditions.
An experimental aeration system designed by the author was operated in the 180,000 ML Eppalock Reservoir for 19 days during March 1977. This mixed the reservoir to the depth of the aerators (24 m) increasing the low 10% saturation dissolved oxygen at this depth to a high 94% saturation thereby changing chemical conditions from reducing to oxidising. As a result the iron concentration in the surface water decreased from 2.04 mg/L to 0.54 mg/L but there was little change in the pre-aeration 0.03 mg/L manganese concentration with this short period of aeration. The iron concentration in the water flowing in the pipeline changed from 1.78 mg/l to 0.57 mg/l.
The problem of pipe flow reduction from bacterial slime growth on the pipe walls is discussed in this paper and examples are given of the use of automatic reservoir aeration to overcome the problem including costs and results.
N. Vitharana, A. Gower, G. Bell and N. Petrovic
Churchman Brook Dam is a 26m high earthfill dam with a puddle clay core and impounds a reservoir of 2.2GL. Various remedial works have been undertaken since completion of construction in 1928. In September 2000, a sinkhole in the right abutment was observed during a routine dam inspection. Following this incident, detailed site investigations were carried out. These investigations revealed that there are soft zones and possibly voids formed in the upper part of the clay core.
A comprehensive dam safety study and a risk workshop undertaken in 2002/2003 showed the dam to be deficient in aspects associated with piping, spillway adequacy and outlet works condition. A rational geotechnical model was developed for the foundation utilising triaxial test data from 1980s and recent investigations. The existing spillway chute will be upgraded with a concrete liner attached to the existing chute incorporating no-fine concrete as a free-draining medium. This paper presents the various aspects of the remedial works currently being designed.
N.M. Nielsen and L.Casey
An energy and water company spends $8 million on maintenance each year. This work is defined and scheduled through a maintenance management system, part of an enterprise solution that cost the company over $2 million for licence fees, management consulting and installation.
The company has an ageing asset base and has been spending $18 million annually on capital improvements. The work activities are selected to meet safety requirements, enhance reliability, improve plant and upgrade customer service, and are defined, prioritised and scheduled on Word and Excel, which are standard applications on the desks of the company’s engineers and accountants.
This company is a composite (typical) of many in the energy and water business.
The most significant business decisions that owners usually have to make are capital spending commitments to modernise energy and water assets. To be successful, strategies have to be devised to meet the overall strategic objectives of the business, and processes adopted based on a fully functional and integrated asset planning system.
‘Aptus’ is a web-based planning application built specifically for asset intensive businesses. It enables a consistent analytical framework using engineering knowledge and the dam owner’s financial criteria, to provide new perspectives and support strategic planning and decision making with triple bottom line reporting. Aptus is a proven resource to maximize the value of the asset portfolio and sustain the business into the future.
Cairn Curran Dam is a 44m high zoned earthfill embankment located near Bendigo in central
Victoria. The dam is owned and operated by Goulburn-Murray Water.
A risk assessment had identified that the junction between the embankment and spillway wall was a weakness in regard to the potential for piping. Initial geotechnical investigations indicated a softened zone adjacent to the foundation.
The conceptual upgrade design was to excavate the downstream slope and place filter material and a rockfill weighting berm. A 2-D slope stability analysis gave unacceptably low factors of safety for this excavation. The three dimensional nature of the embankment/spillway interface and excavation geometry was identified as an important factor in the upgrade design.
A detailed geotechnical assessment was undertaken and a geotechnical model developed that
accounted for potential softened zones adjacent to the spillway wall, along the foundation, and within the embankment.
A 3-D limit equilibrium slope stability program was utilised to analyse the 3-D factors of safety. The
program employed an extension of Bishop’s method of slices to a 3-D ‘method of columns’. A 3-D
finite element analysis was also undertaken to estimate likely deformations of the embankment and cut slope during construction.
The development of the geotechnical model and subsequent analysis allowed the upgrade works to be undertaken with confidence.